Question about Aprilaire 600 Humidifier
Thank you for contacting us. Does your humidistat have a blower activation switch on the lower left hand side of the humidistat? If you do it is our #60 humidistat, and if it is not there you have a #58 humidistat. The R & C are the two connections that supply power to the humidistat to give you the numbers on the digital display. The 60 you wire right into the R & C off the furnace panel. The 58 you need a constant 24 volt and 10 VA power source which you could get by using the transformer off a constant 120 volt power source to power the humidstat. If you are doing this correctly and you still do not get the numbers to show up, then you have a bad humidistat and you need to go back to where you purchased it from and exchange it under warranty provided you used a certified HVAC contractor to do the installation. Our warranty is only valid if you used a certified HVAC contractor to do the installation. If you have any additional questions please contact us at 800-334-6011.
Research Products Corporation
Posted on Nov 16, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 23, 2009 | Aprilaire 600 Humidifier
Jan 15, 2009 | Aprilaire Humidifiers
Jan 14, 2009 | Aprilaire 600 Humidifier
Jan 11, 2009 | Aprilaire 600 Humidifier
Jan 10, 2009 | Aprilaire 600 Humidifier
Jan 06, 2009 | Aprilaire 600 Humidifier
Oct 14, 2008 | Aprilaire 600 Humidifier
Dec 05, 2007 | Aprilaire 600 Humidifier
May 22, 2017 | Aprilaire 600 Humidifier
265 people viewed this question
Usually answered in minutes!