Question about Intertherm Heating & Cooling
Hello,The 90* nozzle is usally installed in miller brand units because of the "short" chamber.The 90* should not cause soot.Soot = not enough primary AIR into the burner mix.If the unit mfg. wants .50/80*a it should be used.#559 might translate into a .65gph input thus overfiring the unit.If a .50gph is installed the AIR mix problem will take care of itself (less fuel).Soot is unacceptable in your (young)3.5yrs unit and should NEVER have soot at all.The problem started when the nozzle was replaced try (insist) on mfg spec. nozzle.
Posted on Nov 08, 2010
Testimonial: "Good advice. My tech will be here tomorrow morning and I have already purchased the proper 50/80 A noozle as required by unit manufacturer. "
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 06, 2015 | Intertherm Heating & Cooling
Dec 23, 2014 | Intertherm Heating & Cooling
Aug 30, 2014 | Coleman Mobile Modular Home Gas Furnace...
Nov 23, 2013 | Heating & Cooling
Mar 23, 2011 | Heating & Cooling
Jan 08, 2011 | Goodman Heating & Cooling
231 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: