Question about Ruud Air Conditioners
I had a RUDD unit installed last year at a condo at the beach. We arrived tonight and only the fan is running. When I go to look at unit outside, it isn't running. We've looked at the fuse box and thought of any way it's not getting power but can't figure it out. I'm sure the last time it was turned on because we do not rent the unit and were here last month but it was still cold and we didn't use it. HELP...we are burning up!
AC Unit humm but fan dosnt tun on unit. I turn the power on and off and can hear it click. Help???
Posted on Jul 05, 2008
Ok it unit is a central I'm suspecting a voltage transformer is defective you see these units need 24v to turn on certain components but if your air handler turns on, your getting 24v to the fan relay, the problem would be elsewhere. if your handy with a volt meter open the thermostat(if applicable) put the meter on ac volts and measure to see if there's 24v between the R and Y terminals
if so your cooling contactor is defective. (If you get 24 v and unit outside dosen't turn on) if there isn't some fuse on the air handler control board blew out.
you can e-mail me @ email@example.com if you need more info
Posted on Jun 16, 2008
Tips for a great answer:
Aug 11, 2011 | Air Conditioners
Jun 01, 2011 | Air Conditioners
Jan 12, 2011 | Ruud UAPA024 Air Conditioner
Jul 15, 2010 | Ruud UBHC Air Conditioner
Jun 18, 2010 | Ruud Central System Air Conditioner
Mar 21, 2010 | Ruud Air Conditioners
Jun 17, 2009 | Ruud UBHC Air Conditioner
Jun 15, 2009 | Air Conditioners
Apr 26, 2009 | Carrier 38CKC036 Air Conditioner
125 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: