Question about Weather King 10AJA4201AH Air Conditioner
The unit outside makes a loud noise & blows cool air. For the last 2 years we have had to put freon in it. We were told we had a leak in the A coil. We just paid someone $996 to fix that. Now our unit is loud & blows cold air & inside is not cooling off. Right now it is 80 degrees in our house & the air conditioner is on & fan is running outside. HELP PLEASE!!
I would take a very close look at every solder joint there is between the inside unit and the outside. If you observe oil at any point it indicates a leak at that point. That is an expensive price for what you say was done. Check your invoice for the amount of refrigerant they or he added to the system. Compare it with the amount stated on the outside unit nameplate. Check for frost on the suction (big line) by the outside unit. If there is frost your coil is frozen up. If this is the case turn the fan on and the cooling off. Allow it to run in this manor for about an hour to defrost the A coil. Then return to the cooling mode.
Posted on Jun 16, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 22, 2014 | Frigidaire FAM157S1A Air Conditioner
Jul 26, 2011 | Ruud Matching Split Air Conditioner
Sep 30, 2009 | Ruud UBHC Air Conditioner
Jul 28, 2009 | Dometic Rooftop RV Air Conditioner
Jun 29, 2009 | Goodman CKL49AR49 Air Conditioner
Jun 29, 2009 | 2006 Volvo S40
Jun 04, 2009 | Heating & Cooling
May 21, 2009 | Heating & Cooling
427 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: