Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
First you are using abnormal wire colors for a furnace. Second.... if you have an air conditioner hooked up to this furnace, you will need to install a jumper wire between rh & rc. I am assuming this is a natural gas furnace. Usually the red wire to R terminals. Usaully the white wire to the W terminal. Take the door off of the furnace. Find the thermostat wire connection in the furnace. What ever color wire is on the R terminal in the furnace should hook to the R terminal on the t/stat. Whatever color is on the W in the furnace goes on the W on the t/stat. Whatever color is on the G terminal in the furnace goes to G on the t/stat. And the Y in the furnace to the Y on the stat. and the G in the furnace to the G on the stat. Most applications use only the R, W, G, & Y ( always put the jumper wire between Rh & Rc)
Posted on Mar 28, 2009
The proper way to do it would be to use a small piece of wire stripped at the ends. Then use a small amount fo solder on each end to connect RC to RH. Or use a small piece of solid(stiff) wire and strip the ends. The wrap the ends around the connector and crimp them to make contact. I would not use a paper clip. A paper clip is not designed to carry 24volt current and could melt.
Posted on Nov 02, 2009
SOURCE: Wiring problem?
Yes to everything!!
You have it figured out!!
Just make SURE that the blue unused wire cannot touch any of the other wires, it will wreck your transformer in a split second.!
I hope that this will help you to solve your problem!
Thanks for using Fixya!!
Posted on Nov 25, 2009
Tips for a great answer:
Aug 30, 2014 | Honeywell RTH3100C - Digital Heat Pump...
Feb 06, 2014 | Honeywell RTH3100C - Digital Heat Pump...
Apr 17, 2011 | Heating & Cooling
Apr 21, 2010 | Honeywell Heating & Cooling
Apr 21, 2010 | Honeywell Heat/Cool Thermostat
Dec 20, 2008 | Honeywell Electronic Programmable...
Dec 02, 2007 | Heating & Cooling
90 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: