Question about Honeywell Heating & Cooling
The reason you do not have power is because you do not have a wire from the "C" terminal in the furnace to the "C" terminal in your t-stat....if you have an extra wire you can hook it to the "C" terminals and it will work...if not then you will have to run another wire of just run it on battery....
The old t-stat did not have that wire...
Posted on Nov 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 12, 2013 | Honeywell Programmable Thermostat Heater
Nov 28, 2010 | Honeywell Heating & Cooling
Nov 27, 2010 | Honeywell Programmable Thermostat Heater
Apr 21, 2010 | Honeywell Heat/Cool Thermostat
Nov 08, 2009 | Honeywell Electronic Programmable...
Jan 17, 2009 | Honeywell Programmable Thermostat Heater
Jan 05, 2009 | Honeywell Programmable Thermostat Heater
Oct 24, 2008 | Honeywell Programmable Thermostat Heater
Sep 02, 2008 | Honeywell Heating & Cooling
Dec 02, 2007 | Heating & Cooling
32 people viewed this question
Usually answered in minutes!