Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
YOU COULD EITHER HAVE A THERMOSTAT PROBLEM OR FAN CONTROL PROBLEM.TURN THE POWER OFF AT THE FURNACE AND TAKE THE THERMOSTAT OFF THE WALL.MAKE SURE YOU MARK THE WIRES SO YOU KNOW HOW TO HOOK IT BACK UP AGAIN.RESTORE POWER TO THE FURNACE.TOUCH THE WIRES THAT WERE HOOKED TO THE R & G TERMINALS ON THE T-STAT TOGETHER AND HOLD THEM THERE.OBSERVE THE OPERATION. WHEN YOU TAKE THEM APART DOES THE BLOWER STOP?TRY IT A FEW TIMES. IF IT CONTINUES TO START AND STOP YOU GOT A BAD T-STAT.JEFF
Posted on Dec 15, 2007
Make sure a back draft in the flue is not happening. Wind can blow it out until the flue heats up. The flame sensor may not be close enough to the burner flame. It may be weak and need to be replaced or if its an optical one it may be dirty and not see the flame very well. Its not wasting much gas but it puts extra wear and tear on the gas controls, is noisy, and, as you said, blows cold drafty air. A gas control system that has issues of any kind is not real safe. It needs to get fixed.
Posted on Jan 08, 2009
There is a small tube that comes off the inducer for cracks or water. If there are cracks then the pressure switch that it is attached to may not be closing all of the time. Also sometimes you can get water in that tubing which will also cause the pressure switch to not close. If thats the case shorten the tube so there is no low droop in it where water can collect. Another thing that I would do is disconnect the tube at the indicer, take a straightened out paper clip or stiff wire and poke it in the nipple on the inducer to make sure it is clear too. Let me know if any of these work. There may be other things we can do.
Posted on Jan 19, 2009
Tips for a great answer:
Dec 21, 2014 | Fasco Intercity Heil / Tempstar Furnace...
Aug 17, 2014 | Heating & Cooling
Jan 28, 2014 | Office Equipment & Supplies
Oct 17, 2013 | Carrier Icp Heil Tempstar Furnace Blower...
Jan 06, 2013 | Heating & Cooling
Dec 31, 2012 | Fasco Furnace Draft Inducer Heil Quaker...
Nov 12, 2012 | Heating & Cooling
Aug 20, 2012 | Heating & Cooling
Jun 20, 2010 | InFocus ScreenPlay 5000 Multimedia...
Nov 11, 2009 | Heating & Cooling
106 people viewed this question
Usually answered in minutes!