Question about Goodman Heating & Cooling
The pressure switch will look something like this
They do go bad sometimes or the tubing may get kinked or have water in it....check all of the tubing that goes to it...
To test it you will need an OHM meter and see if the contacts close if you pull a vacuum on it...
I often just s u c k lightly on it....to see if I hear it click faintly....
but then that is not fail proof either... it can trip that way but not with the vacuum from the fan....
They are not a high $$ item and I would just try replacing it if nothing else seems to be wrong...
Posted on Nov 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 23, 2011 | Goodman GMS80903BNA Heater
Jan 02, 2011 | Goodman GMS90703BXA Heater
Jan 18, 2010 | Goodman Heating & Cooling
Jan 11, 2010 | Goodman Heating & Cooling
Jan 09, 2010 | Goodman GMS90703BXA Heater
Jan 06, 2010 | Goodman GMS90703BXA Heater
Dec 01, 2009 | Goodman Heating & Cooling
Oct 20, 2008 | Goodman GMS90703BXA Heater
Sep 18, 2007 | Goodman GMS90703BXA Heater
113 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: