Question about Heating & Cooling
You need to see if you have power to thermostat. If you have a volt meter /multi-meter and know how to use it you can check it.Remove cover from thermostat and see if it has a mercury switch. This will be a small glass vial that is connected to temperature setting lever. if you move heat setting up or down the glassvial will move with it and you should see a small spark inside.I should back up here because I assumed that you have a older style manual thermostat. If you have a programmable t-stat disregard . Either way if you are sure you have your t-stat in the proper position to call for heat and it's not working. If you are mechanically inclined you can carefully remove cover from t-stat and remove 3 or 4 small screws that mount it to wall. Be careful as the control wires are very small and may break, carefully remove red and white wires . The terminals should be marked as R and W. If you jumper red and white wires together furnace should come on. If you have a multi-meter you can check for voltage across r and w withot removing from t-stat. You should have about 24 volts a.c. If you have proper voltage or if unit works when you jumper r and w then you need to replace thermostat.If you don't have proper voltage there you will need to check transformer,control board or wiring. Hope this helps. Thanks.
Posted on Nov 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 20, 2013 | Heating & Cooling
Oct 13, 2012 | Honeywell Programmable Thermostat Heater
Oct 02, 2012 | Microwave Ovens
Jun 25, 2012 | Hardware & Accessories
Jun 06, 2012 | Goodman Heating & Cooling
948 people viewed this question
Usually answered in minutes!