Question about Goodman GMS80453ANA Open Flame Mid-Size Heater
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Ok, you either have a inducer fan issue or a pressure switch issue or a plugged vent pipe. The inducer turns on to establish a draft for the exhaust. If it is not working you will get this error code. If the pressure switch does not sense pressure caused by the inducer, it will give this code. If either the intake pipe or exhaust pipe is blocked (even y just a little) it will give you the same error code. If the condensate hose or receptical is plugged, again it will give you this error code. Good Luck!
Posted on Oct 21, 2008
When you call for fan in auto ensure your getting 24 volts at pin on control board, if it is not energizing then there is a problem with the relay.. Before you change out the expensive control board, try the therm..
Posted on Dec 09, 2008
should be installed with
1) red to rc and jumpered to rh
2) green to g
3) yellow or blue to y
4) white to w
to test: remove t-stat connect white and red - furnace should operate normally unitil you disconnect.
if it does replace t-stat
Posted on Oct 27, 2009
Tips for a great answer:
Oct 24, 2013 | Heating & Cooling
Jan 12, 2011 | Goodman Heating & Cooling
Nov 05, 2010 | Hunter Fan Company 5/1/1 Programmable...
Oct 19, 2010 | Heating & Cooling
Oct 03, 2010 | Honeywell Electronic Programmable...
Dec 05, 2009 | Honeywell Programmable Thermostat Heater
Nov 30, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 27, 2009 | Honeywell Programmable Thermostat Heater
Nov 19, 2008 | Heating & Cooling
Nov 12, 2008 | Honeywell Programmable Thermostat Heater
117 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: