Question about Goodman GPC1342H21A Air Conditioner
Make sure the fan switch on the t-stat is not set to the "on" position....
If not then the fan or fan and limit switch in your furnace may be bad.....
or sometimes if your unit has a fan relay on the control board that will go bad and then the whole board needs to be replaced...
Posted on Nov 07, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 11, 2017 | Honeywell Heating & Cooling
Feb 09, 2011 | Heating & Cooling
Nov 18, 2017 | Honeywell CT87B ROUND HEATING&COOLING...
Dec 19, 2010 | Goodman PHKJ024-1 Air Conditioner
Dec 31, 2017 | Goodman GMS90703BXA Heater
Sep 03, 2010 | Carrier Heating & Cooling
Dec 11, 2009 | Goodman Heating & Cooling
Jan 27, 2009 | Heating & Cooling
Jan 12, 2009 | Honeywell Programmable Heat Pump...
May 23, 2018 | Heating & Cooling
May 23, 2018 | Coleman Heating & Cooling
41 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: