Question about Traulsen G10010 Refrigerator
Unit will not cool at all, refrigerator is too warm.
Full service call video. Traulsen Refrigerator. Found bad motor and replaced. I hope it will help.
Posted on Dec 24, 2016
Don't know this maker or model but if it is constructed like most modern units, the evaporator is under the bottom of the refrigerator and uses a fan to circulate air past it to dispose of heat taken from inside.
If this fan fails, either completely or because of excessive dust, the coolant is circulating via the compressor but the removed heat from the inside is not being removed from the evaporator.
Check for the presence and operation of this fan.
If failed, it can cause the problem you are having.
Most are accessible from the rear of the unit and are plugged in to permanent wiring so replacement might be quite easy.
Posted on Jun 15, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 16, 2013 | Traulsen G20010 Commercial Refrigerator
Jul 19, 2011 | Traulsen VPS90S
Feb 22, 2011 | Traulsen G20010 Commercial Refrigerator
Oct 28, 2010 | Traulsen Refrigerators
Jul 31, 2010 | Traulsen G20010 Commercial Refrigerator
Mar 23, 2010 | Traulsen G20010 Commercial Refrigerator
Feb 10, 2010 | Traulsen G10010 Refrigerator
Jun 17, 2009 | Traulsen G10010 Refrigerator
Jul 16, 2008 | Traulsen G10010 Refrigerator
243 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: