Question about Heating & Cooling
Try this----turn furnace off at stat and unplug furnace for 10 minutes. Plug it back in, the combustion and blower motor may both kick on for 2 minutes or so or not. Turn t-stat to heat and turn up stat to highest setting. Hurry out to furnace and you should hear the combustion motor(little motor piped to flue) kick on, then wait for a "click" next you should see a glow from the igniton element, then another click, next will be the gas valve opening. If no ignition, it will try 3 times and then lock ur *** out, and just turn on the blower just as a precaution. If you dont see the glow plug glowing after the first click, replace the $20 glow plug and you should be good to go. The glow plugs crack, and this is what breaks the connection. If you gas valve has a knob, and says pilot----turn the valve to pilot, push down on the knob, light the pilot and hold down knob for 2 minutes to heat up flame sensor. Make sure the t-stat is all the way down or off. After 2 minutes of holding pilot knob down, let go and your pilot should be still lit, if it is, then turn gas valve to ON and then turn t-stat up to kick on furnace. If ur pilot doesn't stay lit, get a new thermal couple and replace it-$12 bucks. Good luck and let me know how it went. email@example.com
Posted on Nov 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 09, 2014 | Amana Heating & Cooling
Jun 05, 2017 | Heating & Cooling
Nov 04, 2012 | Heating & Cooling
Oct 10, 2012 | Amana GMVC80905CX Gas Furnace
May 31, 2010 | Heating & Cooling
Jan 11, 2010 | Ruud UBHC Air Conditioner
Jan 04, 2010 | Amana Comfort Zone 12M32PBEH Air...
Nov 15, 2008 | Amana Heating & Cooling
244 people viewed this question
Usually answered in minutes!