Question about Cfm Daikin R410a Split System Air Conditioner
More info needed. try fixing the problem then turn unit of at the main power wait for 10 mins then turn on? whats the error code?
Posted on Nov 09, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
you cannot fix this mate... you will need a fridge mechanic.. try cleaning your filters id say that's your only chance
Posted on Nov 11, 2009
SOURCE: I have a Daikin split
E5 Outdoor activation of compressor over heatprotection or motor lock
Check condenser coil. If dust blocked-clean it.
Check out door fan motor is working. If not replace capacitor or motor.
Check compressor-gradually amps increasing-replace capacitor.
Check for gas pressure. No gas also gives over heat compressor.- Leak test and rectify.
Posted on Jan 16, 2011
Tips for a great answer:
Jan 29, 2016 | Cfm Daikin R410a Split System Air...
Sep 30, 2015 | Inverter Heating & Cooling
Jan 03, 2015 | Heating & Cooling
Sep 20, 2014 | Heating & Cooling
Apr 10, 2014 | Heating & Cooling
Sep 20, 2013 | Daikin ARC452A9 Replacement wireless...
Mar 22, 2012 | Cfm Daikin R410a Split System Air...
Mar 30, 2011 | Cfm Daikin R410a Split System Air...
Jan 16, 2011 | Heating & Cooling
Jul 02, 2015 | Cfm Daikin R410a Split System Air...
Jul 28, 2014 | Cfm Daikin R410a Split System Air...
5,946 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: