Question about Goodman GMS80903BNA Heater
The roll out switch is often located where you could easily have hit the wiring as you changed the ignitor. It is located just outside and over the burners so that if the flame "rolls out" it will sense the heat and interrupt the ignition process.
Check the continuity across the switch, also check the wires to make sure that you have not knock any off accidentally or that there are no loose connections...
You are getting this code because of a open condition in this circuit.
Posted on Nov 06, 2010
There is a possibility you knocked the wires off.
Posted on Nov 05, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 27, 2014 | Goodman GMS90703BXA Heater
Nov 11, 2013 | Patton Electric Patton PUH680-U Electric...
Sep 24, 2012 | Goodman Manufacturing Goodman R410A 13...
Jan 23, 2011 | Goodman GMS80903BNA Heater
Dec 14, 2010 | Heating & Cooling
Dec 03, 2010 | Goodman GMS80903BNA Heater
Apr 13, 2009 | Heating & Cooling
Feb 28, 2009 | Goodman GMS90703BXA Heater
Oct 07, 2008 | Goodman GMS80903BNA Heater
Oct 20, 2009 | Goodman GMS80903BNA Heater
178 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: