Question about Amana Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Amana 80SSE Furnace
Not much info to go on, but lets look at a few possibilities. Your thermostat could be turned to the ?Fan On? setting, make sure you put it in the ?Auto? mode. Or it could be bad, or there could be a short in the wiring. Open up the access panel on your furnace. Lets eliminate the thermostat from the equation by disconnecting the red, white and if you have a yellow wire at the furnace. Mark down which wire went where. The furnace will have a door safety switch that will have to be taped temporarily closed to test the furnace. With a short piece of wire (2-3" long), strip off 1/2 inch of the insulation on both ends. Secure one end on the R terminal where you removed the red wire from your thermostat. Take the other end and touch the G terminal on the same electrical board. Your fan will start. Don't worry about an electrical shock, the voltage is only 24 volts. Now with one end still attached to the R terminal, touch the W terminal where the white wire was attached. The furnace will now try to fire up. Hold it there until you see that it did start. If you did this and had success, I would say it was your thermostat or the wire going to it. Last resort would be a bad control board. If you want, you can do test your thermostat wiring by removing the thermostat from it's mounting plate. Put all wires back where they were on the furnace. Make sure the access door is back in place and secure. Take that same jumper and jump across the red and white wires on the mounting plate. Again the furnace should start up. Have a helper jiggle the thermostat wires where accessible when the furnace is running and see if it remains on or shuts off. If everything checks out, replace the thermostat. Good Luck!
Posted on Oct 08, 2007
SOURCE: I have a Trane gas
almost a classic sign of a bad gas valve. pilot is lit so gas is available. FAN COMES ON AND 24 VOLTS TO gas valve so there is a call for heat . gas valve doesn't open so it looks like its bad.
Posted on Nov 10, 2008
SOURCE: Amana furnace will not light.
Try tapping firmly on the gas valve while it is trying to open. If it ignites, you will definately need a new gas valve in the near future (but this little trick might get you by for a while). If not, try using a meter, to make sure you are getting 24v to the gas valve. If you are getting 24v to the gas valve and it is not opeining, you have a bad gas valve. If you are not getting 24v to the gas valve, you have a different problem like a bad transformer, ignition box, or circuit board.
Posted on Dec 16, 2008
Tips for a great answer:
Nov 25, 2012 | Honeywell VisionPRO Thermostat TH8110
Oct 10, 2012 | Amana GMVC80905CX Gas Furnace
Feb 28, 2011 | Heating & Cooling
Feb 09, 2011 | Amana PTH123B25AJ Heat Pump Air...
Sep 11, 2010 | Amana Dryers
Dec 12, 2009 | Heating & Cooling
Jul 02, 2009 | Ruud UBHC Air Conditioner
71 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: