Question about Heating & Cooling
2 TON SPLT UNIT MITSUBISHI MODEL NO MU24AV
Building hight is about 16 meters, condensing unit at roof,
in installation manual hight is 15 metes with 30 meters pipe run and pipe size is 5/8", and it is not mention that there will be any oil retrun problem
1.Do we need to fix a p oil trap at riser or no need?
2. Do we need to change suction line size or keep same size?
3 if same size of piping and with out oil trap will system works without any problem?
After installing the system would I advice to measure pressures. By the lenght of pipes and hight difference of the units will there be a pressure drop. Be aware if more pipe lenght as the original is used, oil should be added to the system (oil is sticking in the pipes, the more lenght and traps, the more oil will be in the pipes instead of in the compressor).
Posted on Jul 26, 2008
Pipe size is okay, not that I know any better than the manufacturer, but I would recommend at least two and possibly even three oil traps in the vapor line on the way back up.
Posted on Jun 15, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 14, 2015 | Amana Goodman R-410A Heat Pump Condenser 2...
Jul 18, 2014 | Rheem 14AJM49A01-RHLLHM4821JA 4 Ton 16...
Jun 28, 2010 | Ruud Handler Air Conditioner
Aug 13, 2009 | Carrier Heating & Cooling
Jun 07, 2009 | Heating & Cooling
811 people viewed this question
Usually answered in minutes!