Question about Ruud UBHC Air Conditioner
I have a RUUD heatpump/AC unit with manual thermostat.
Inside unit is UBHC-17J11SHG, outside unit is UPMC-030JAZ, thermostat is T874R1434.
New thermostat is Honeywell Vision Pro 8000 series (TH8320U1008).
When I remove the faceplate on the existing thermostat, I see the following wires connected on the left side from top to bottom:
Black (or Dk. green).
Connected the the mercury thermometer is white, blue and yellow on top.
Connected to the bottom is red and black (or Dk, green),
I need to know what wires go where on the Honeywell wiring block.
Hopefully there are markings on the old t-stat as to what terminal is what.
on the honeywell 8000 use the heat pump labeling and then the standard wiring would be
There should not be a bare wire, it probably just has the insulation stripped back way too far.
You should probably open the furnace and compare the terminal label in the furnace to the wire color. normally yellow and blue pass through the furnace and are wire nutted to wires going to the outdoor unit. In the furnace the white wire will connect to the w or w1 terminal. also, you will need to set the Honeywell stat to have the following parameters.
other parameters that I did not specify, you may read the manual and make your own decision but I recommend factory settings for the other parameters
Posted on Jun 18, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 11, 2014 | Ruud UBHC Air Conditioner
Jun 26, 2012 | Ruud UBHC Air Conditioner
Feb 02, 2010 | Ruud UBHC Air Conditioner
Jan 06, 2010 | Ruud UBHC Air Conditioner
Apr 07, 2009 | Ruud UBHC Air Conditioner
Jan 05, 2009 | Ruud UBHC Air Conditioner
Dec 13, 2008 | Honeywell Programmable Thermostat Heater
Jun 06, 2008 | Ruud UBHC Air Conditioner
824 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: