Question about Carrier LFP Humidifier
Check all supply registers of the unit, which are wide and flat and located on your walls. Make sure that they are open and unclogged. Inspect the cleanliness of the unit and of the distribution pad.
Observe the fan's function. Spray lubricant on on the motor shaft of the fan unit to ensure it rotates properly.
Take off the small pipe between the solenoid valve and the humidifier and check if the opening is blocked. If not, you may need to replace the solenoid valve.
Check whether the thermostat has been set to a heat position and that the temperature is set above the room temperature. Check that the furnace is getting power supply and the circuit panel to see if all the circuit breakers are in an "ON" position. Check all the return air grills on the wall, make sure they are not blocked.
Check whether the thermostat is set to "COOL." Check also the circuit breakers and that they are in an "ON" position. Make sure that the blower motor in the furnace is running, as it should be when the thermostat has been set in a cool position.
Posted on Nov 05, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 08, 2015 | Carrier Humidifiers
Jan 21, 2012 | Carrier LBP Humidifier
Feb 23, 2011 | Carrier LBP Humidifier
Jan 30, 2011 | Carrier LFP Humidifier
Jan 19, 2011 | General Filters 1042-LH Humidifier
Dec 17, 2010 | Carrier Humidifiers
Mar 10, 2010 | Aprilaire Humidifiers
Mar 03, 2010 | Aprilaire 600 Humidifier
Nov 22, 2008 | Carrier SBP Humidifier
Jan 26, 2013 | Carrier LFP Humidifier
Apr 27, 2012 | Carrier LFP Humidifier
Jan 15, 2011 | Carrier LFP Humidifier
828 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: