Question about Carrier Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
if your power vent moter is not running you should not have have glowing ignitor.Frist the vent moter must close an air prove switch in series with the idnitor .seems you have a stuck air prove switch.Its the one with a hose attached
Posted on Apr 07, 2009
SOURCE: power up unit and thermostat,
You have a short circuit, which is obviously dangerous. Your blower motor is controlled via a 24VAC control circuit, but is 120VAC. The circuit board and gas valve are probably history, but it needs to be troubleshot to determine the scope of the damage.If you remove T stat you will see several colored wires. The red and green wire when touched together should cause your fan blower to run. If that works when you bypass t stat the t stat is gone. The red to white will open your gas valve on your heater. The red to the yellow or blue will start your AC compressor or condenser fan motor. Be careful with the yellow and blue wires as one is actually a neutral and one goes to the AC contractor on your condenser unit contractor. Hope this helps!
Posted on Aug 02, 2011
Tips for a great answer:
Jun 02, 2014 | Intertherm Heating & Cooling
Mar 22, 2013 | Heating & Cooling
Nov 20, 2011 | Heating & Cooling
Jun 26, 2011 | Heating & Cooling
Feb 20, 2010 | Dryers
Jan 22, 2010 | Goodman Furnace Draft Inducer Blower ...
Nov 14, 2009 | Honeywell Programmable Thermostat Heater
Oct 31, 2009 | Heating & Cooling
Jan 16, 2009 | Heating & Cooling
May 01, 2008 | Heating & Cooling
161 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: