Question about Heating & Cooling
Count the number of flashes and consult your manual as to what the flashes mean. The blower access door may show the faults codes. What you probably have is a contaminated flame sensor or maybe a rollout switch tripped due to rusty burners or air restrictions in your heaters vent pipe. Or a cob web blocking the tubing between the proving switch and inducer fan. Use a dry brillo pad to clean the flame sensor. Check the reset buttons on your limits clear cobwebs out of vents clean rusty burners. This video shows a typical new fangled gas furnace in action:
This video shows how to clean that pesky flame sensor:
Having an understanding of how they work can help you duagnose any of these late model wonders.
If you need further help, reach me via phone at https://www.6ya.com/expert/dan_73bbd84fe1d95b61
Posted on Nov 02, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 19, 2016 | Goodman Heating & Cooling
Oct 30, 2016 | Goodman Heating & Cooling
May 18, 2015 | Goodman Manufacturing Goodman GPH1330M41...
Oct 06, 2014 | Goodman Heating & Cooling
Mar 25, 2014 | Goodman Heating & Cooling
Jul 08, 2012 | Goodman CPLE24-1 Air Conditioner
Aug 17, 2009 | Goodman CKL60AR60 Air Conditioner
Jun 13, 2009 | Heating & Cooling
Dec 12, 2008 | Goodman GMS90703BXA Heater
695 people viewed this question
Usually answered in minutes!