Question about Heating & Cooling
Yesterday it was only putting out faintly cool air. I turned the unit off, hosed it out, changed fuses and turned it back on. It worked perfect, until now.
It started to do the same thing so I turned it off and checked the fuses, searched for any loose wires.... I'm lost. Now the fan kicks on and off but the unit itself doesn't seem to be kicking in.
Hmm It's passable that the condenser fan motor is not spinning at speed or is running for a period of time and over heating and the Condenser fan motors internal overload protection trips and takes it of line shortly thereafter, of course, the compressor internal overload trips and takes it of line. Spraying with the water hose sped up the cool down on the internal overloads but I'm afraid it probably didn't do much to help the original problem. You could try replacing the Fan condensing motor capacitor-(it's listed on the side of the motor if the capacitor cant be read) and oiling the motor if it has oil ports (2 small plugs located along the perimeter of each end of the motor). If the motor can be oiled and you replace the capacitor theres a fair chance you might get by another year without replacing the condenser fan motor. Charged capacitors pack a nasty jolt so be careful, hope this was helpful, GL!
P.S. If it is the cond. fan motor and you replace it be sure you get a sealed outdoor rated cond. fan motor and the appropriate rain guards are installed.
Posted on Jun 12, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 04, 2014 | Heating & Cooling
Jan 05, 2012 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 02, 2011 | Heating & Cooling
Jun 02, 2011 | Carrier 38CKC024 Air Conditioner
Apr 27, 2010 | Carrier 38CKC024 Air Conditioner
Oct 11, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Aug 04, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Apr 14, 2009 | Carrier 38CKC042 Air Conditioner
Jul 19, 2008 | Carrier 36KCARMS Air Conditioner
1,077 people viewed this question
Usually answered in minutes!