Question about Heating & Cooling
I bought a Camping trailer that has a Coleman Tsr Mach 3 Air conditioner on it. I can run the fan on it on High, or Low for hours. When I put it in the "cool" position it cuts off after about 10 min. This happens wheather it is in the high or low setting. I believe I'm having the same problem. I just bought a used travel trailer equipped with the Coleman TSR Mach 3. We started using the a/c this past Saturday morning and was working fine until about 2:00 pm when the sun was directly over the camper. Then the compressor kept shutting off and when it tried to kick back on it just couldn't. So we turned it off and when the sunset and everything cooled off we started it back up and it ran all night long because we stayed in it just to make sure. We left it running all day Sunday until 2:00 pm came again and the compressor shut off again. Again when it cooled it ran fine. Now two days later it will run for about an hour and it will cut off and when it tries to come back it just cant't make it. Nothing is tripping inside the camper or the house, water is also dripping from atop the camper so I don't guess it is freezing up. Could this be something major? Please help I hate to buy a new one.
I don't think you need a new one just a good cleaning and service. The unit has a liquid high temperature line near the compressor with a fan blowing outside air across it this coil gets clogged over time with air-borne dirt and pollen and leaves and such and must be cleaned regularly or the unit will be unable to remove the heat from the coil and during the peak demand (3pm) the circuits that protect the compressor and the trailer wiring from being overloaded and burning or melting will trip. From what you have described it sounds like the RV is working as it should with a condenser coil that needs to be cleaned. GL and happy camping!
P.S. I've only serviced the occasional RV unit but in those cases I laid a piece of plywood on top of the Rv for work platform removed the retaining screws from the top cover and used a spray bottle with a good heavy foaming cleaner a shop-vac and a brush to get the job done.
Posted on Jun 11, 2008
My Coleman mach air conditioner on my pop up needs to be replaced, per a friend. He when the freon is gone, so is the unit. Is their a part that can be replaced and just add freon.
Posted on Feb 09, 2009
the fan motor bearings need lub....the shaft has a tiny access hole to put some oil into. because the fan shaft is slowing down, it is putting more strain on the voltage current, and eventually the internal breaker shuts down the ac........plus your condenser is not getting enough air accross it, compressor heats up, and it too will shut the unit down......older units have to be oiled every year, and eventually it too will fail, and a new blower motor assembly is needed or replace the ac unit.....blower motor units are around $130....now you install it or pay to have it done at around another $150 labor,,,,,try yourself, if it fails then call the tech........let me know ..ray..firstname.lastname@example.org
Posted on Dec 31, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 20, 2010 | Coleman Mach III Air Conditioner
Jun 28, 2009 | Coleman Mach 15 Air Conditioner
Jun 22, 2009 | Coleman Mach III Air Conditioner
Jun 25, 2008 | Coleman Mach 15 Air Conditioner
May 20, 2008 | Coleman Mach 15 Air Conditioner
2,403 people viewed this question
Usually answered in minutes!