Question about Amana PTH123B25AJ Heat Pump Air Conditioner
The hoses coming out of my unit are frozen over and I'm getting no air conditioning inside my house
You are going to have to increase the amount of heat absorbed by the evaporator coil on the indoor section of your system. First change the filter. Second turn the power off to the outdoor section and leave the indoor fan running until all the ice on the evaporator coil has thawed this could take a few hours. Third you need to verify that you are getting adequate airflow across the indoor evaporator coil and the outdoor condenser coil both fans should be spinning at full speed and airflow should be unobstructed by dirty coil fins or debris Hopefully after you've done this you will have cold air blowing inside and the larger of the two lines entering the unit outside will be cool to the touch but not frozen or even frosted regardless of run time and the small one should be the slightly warm but not hot. If the larger line continues to freeze then it could indicate a number of problems but essentially your condensers cooling capacity is outrunning your evaporator coils ability to absorb heat from air stream circulating in your home.Hope it works out for you GL!
Posted on Jun 12, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 15, 2011 | Ruud Heating & Cooling
Sep 10, 2008 | Amana Heating & Cooling
on May 11, 2010 | Heating & Cooling
May 27, 2010 | Amana AP095R Portable Air Conditioner
Jan 12, 2010 | Amana PTH123B25AJ Heat Pump Air...
Jun 28, 2009 | Amana PTH123B25AJ Heat Pump Air...
Jun 22, 2009 | Heating & Cooling
Aug 25, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 02, 2008 | Amana PTH123B25AJ Heat Pump Air...
Feb 02, 2016 | Amana PTH123B25AJ Heat Pump Air...
188 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: