Question about Heating & Cooling
The fan on the inside is on and blowing but the one on the outside isn't. There is no leak and the breakers is fine. I changed the filter on the inside of the house yesterday morning. and i also cut the unit off since 5pm yesterday just in case it is frozen on the outside. Could this be the problem that its not cooling. I was going to try to cut it on again today when I get off work to see if it will cool
The green cool light is blinking and ac/is not cooling well.
Posted on Jun 22, 2009
Ok, there should also be a service disconnect near the condensing unit usually a 6'x8-10" or so grey box, you need to check this and make insure that your 220v line voltage is getting thru. Sometimes this disconnect is a breaker sometimes fuses and sometimes just a bar type plug ( if the disconnect is tripped the problem is likely a clogged condenser coil, proper cleaning will be needed to prevent it from tripping again) If this is not tripped and you are getting 220v to your condenser then you need to confirm that you are getting the 24v control voltage to the compressor relay from the transformer in the indoor section. If the indoor fan can be controlled at the thermostat it proves that your transformer is good and you have 24v available, you should be able to hear and see (if your looking at it) the compressor relay engage when the thermostat is set to call for cool and the compressor delay on circuit has expired (usually 5 min). If the relay is not engaging then look for a wiring problem between the condenser and the furnace. Do you have dogs that run near the condenser? I often find Improperly secured t-stat wires getting pulled loose or chewed up by the family pet. You should have found the explanation for the fault at this point GL!
Posted on Jun 10, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 19, 2012 | Ruud Central System Air Conditioner
Aug 23, 2011 | Goodman CKL62AR61 Air Conditioner
Jun 19, 2011 | Ruud UAMB Air Conditioner
May 22, 2011 | Heating & Cooling
Jun 12, 2010 | Ruud UAKA018 Air Conditioner
Jul 20, 2009 | Amana ABC2037SS Air Conditioner
Jun 15, 2009 | Ruud UBHC Air Conditioner
Jun 15, 2008 | Weather King 10AJA4201AH Air Conditioner
Jun 08, 2008 | Goodman CLQ36AR49 Air Conditioner
May 20, 2018 | Coleman Heating & Cooling
387 people viewed this question
Usually answered in minutes!