Question about Heating & Cooling
The compressor was never bolted down and now the copper pipe has broken. Is this worth fixing or not ? If it is worth fixing, how much does something like this cost?
If this would be worth fixing would depend on how long the unit ran after the tubeing was broken and how long it has been open for to determine if any contaminants were introduced into the system. A good technician would come out and braze the lines back togather, bolt down the condenser, purge the unit with nitrogen, and pull a deep vaccum before recharging the system. If this were done and your system worked fine which should be the case. It would save you the cost of a new condenser.
Posted on Jun 10, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 06, 2016 | Goodman Heating & Cooling
Sep 01, 2014 | Heating & Cooling
Jul 15, 2011 | Coleman Heating & Cooling
Nov 22, 2009 | Coleman Powermate 27 Gallon Air Compressor
Sep 20, 2009 | Freezers
Jul 27, 2009 | Coleman Mach III Air Conditioner
Apr 27, 2009 | Coleman Heating & Cooling
Jul 01, 2008 | Coleman Mach 15 Air Conditioner
87 people viewed this question
Usually answered in minutes!