Question about Weather King 10AJA3601AH Air Conditioner
I live in Brooklyn, I just moved in to a condo that has a Weather King. It is a new condo, and the model is new. I moved into the condo 1 1/2 months ago, and no one else has lived here before me.
The air conditioner initially blew very cold air. Now, it blows fan air mixed with the cold. It is very unpredictable. Any idea?
Possible causes are dirty filters, dirty condenser coil, dirty evaporator coil, or low referigerant charge. Any one of the conditions will affect heat transfer.
Check the filters in your indoor unit, If they seem to be clean and replaced on a regular basis, your evaporator coil is probably in good shape. Unfortunatley on some Weather King models even checking the evaporator coil is not possible due to the extensive amount of referigerent lines that block access to the coil without some major work including evacuating the refrigerant.
The most likely cause is a dirty outdoor condenser coil. On weather king models you will have to remove the casing that surrounds the coil because is is built in such a way that the condenser coil cannot be properly cleaned with the casing in place. Once it is removed make sure breaker is switched off and clean the coil with a water hose.
If your outdoor coil is not dirty then it is a refrigerent problem.
Posted on Jun 06, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 13, 2014 | Weather King Heating & Cooling
Aug 17, 2012 | Weather King 12AJA6001AH Air Conditioner
Apr 07, 2017 | Ruud Matching Split Air Conditioner
May 10, 2012 | Weather King 10AJA1801AH Air Conditioner
Aug 09, 2011 | Weather King Heating & Cooling
Aug 30, 2010 | Weather King Heating & Cooling
Jan 11, 2010 | Weather King 12AJA4801AH Air Conditioner
143 people viewed this question
Usually answered in minutes!