Question about Haier Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You need to call for for a qualified technician oil residue is a sign that your unit have leaking, your unit is out of refrigerant.
Posted on Dec 31, 2007
You hear the compressor kick in (Hum) but no fan comes on? Will the fan come on when just in fan mode, not cool, or do you have that set-up?
Posted on Aug 14, 2008
It is possible that it's the thermostat. When you turn it into cool mode, does the unit come on at all or is it silent? If nothing is coming on, then it's likely it's the tstat. Did the tech check the refrigerant charge while he was there? He should have checked it with the auxillary heat off and the unit just in heat mode. Make sure that the condenser unit outside is coming on when you are calling for cool, If you turn it on and everything comes on, go outside and put your hand on the large copper pipe coming into the unit. In cool mode, this pipe will be cold to the touch and in heat mode, the pipe will be warm to the touch. There isn't much you can do on your own with the exception of changing the tstat. If you can answer some of the questions I have posed, I can try and give you some more answers. Just remember that a check up doesn't mean its a guarantee that something won't happen the next day, it's just that everything was in working order at the time of the checkup.
Posted on Mar 21, 2009
I think the wiring diagram is on a printed sticker on the side of the water collector, just pull it out of the right side as you look at it. There should be one on there hope this helps as i have the same unit in the other room. regards Richard
Posted on May 29, 2009
The fan motor is getting hot and going off on the internal overload in the motor.
This is caused by either a low voltage, a bad capacitor, or tight or dry bearings in the motor.
To check the bearings turn the power off to the unit, then spin the fan blade if it spins freely then the bearings are ok.
To check the capacitor you will need some kind of tester or you can buy a capacitor and replace it, that's what a lot of people do. They usually don't cost very much.
To check the voltage you will need a voltmeter and measure the volts at the unit.
Posted on Jun 09, 2009
Tips for a great answer:
on Dec 13, 2009 | Heating & Cooling
Jul 21, 2015 | Haier HPY08XCM 8,000 BTU Portable Air...
Aug 26, 2013 | Haier Cpf12xhl-lp Commercial Cool Portable...
May 31, 2012 | Haier HPM09XC5 Portable Air Conditioner
Jul 21, 2011 | Haier Heating & Cooling
Jul 14, 2011 | Danby DPAC13009 Air Conditioner
Sep 27, 2010 | Haier Portable Air Conditioner, Electronic...
Jun 27, 2010 | Heating & Cooling
Dec 13, 2008 | Amana Haier AP125HD Air Conditioner
May 10, 2018 | Haier Heating & Cooling
156 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: