- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Hi Jessica Yacopino - Generally speaking, Frigidaire air conditioners timer option typically have the same procedure. The unit must be in the ON position for the timer delay stop option. For delay start, the unit must be in the OFF position. First, press time button. Then to adjust timer setting, tap or hold the UP arrow or the DOWN arrow to change delay timer at .5 hour increments, up to 10 hours, then by 1 hour increments up to 24 hours. The control will count down the time remaining until start (8, 7.5, 7, etc.). The Delay Start mode automatically selects cooling with maximum Fan Speed. The temperature maintained will be the same as previously set. To change the set temperature, press "COOL" then Up or Down arrows until the desired temperature is indicated on the display. After 5 seconds, the control will automatically change the display back to the hours remaining until the unit will start/stop. PRESSING the unit On/Off button at any time will cancel the Delay Start/Stop function. The Delay Start/Stop Feature will work until the unit either starts or stops. Once that happens the above steps have to be repeated again.
Maximum models and brands having 24 hrs timer. And yours also one of that. If you have clock in your remote keep in what time it should be on and off. If no clock, Press timer on it display as 00.00. Press < or > till you get 24.00. Helpful?
From a loose wire, replacing the contactor to now the
ductwork needs to be sealed. They should have told
you that it needed to be sealed in 2006.
If your unit worked fine in 2006,2007,2008,2009 and occasionally this summer. Tell them to start with the basics and replace your thermostat. Buy a digital thermostat and set it next to your house thermostat
and then tell me how many degrees seperate the two.
Have them check the blower speed to make sure you
are getting between 14-20 degrees across the coil.
If I see a code blinking and all is normal as far as I can tell it means something is in a time out mode and counting down to energize. This may not be the case but let it run and blink for a few hours and see if it comes on.
Mark your watch so you can see how long it takes to change or start.
If it does start then you know about how long it will take to recycle.
Assuming you have changed the batteries in the remote (if you have such), and it does this again do not use the remote again, if possible. Try it with manual only. Remote - remove batteries, this will eliminate the remote as the cause.
Next is find the legend of the codes for your unit. Sometimes they are located by the wire diagram on the unit its self, under the wire terminal panel.
If this helps you please rate me as high as possible. If it gets you on the track and need more help tell me what you did and what you found, post it and I'll post back asap. Thanks for using fixya. and Good Luck.
The e1 code is a demand to clean the filter. It means the unit has been running for 720 hours. It does not mean anything is broken...unless it hasn't been running for 720 hours. That would mean the "clean the filter" timer is broken! There are 2 reset methods.
1) Unplug the machine. Hold down the power button while plugging it back in and wait until it beeps (for about 5 seconds). Let go of the power button. Unplug the machine again, then plug it in and try to use it as an air conditioner.
2) Unplug the machine. Hold down the Mode button while plugging it back in. Keep the mode button pressed until it beeps (for about 3 seconds). Let go of the mode button. The machine will start. Turn it off by pressing the power button. Resume trying to use it as an air conditioner.
If neither of these work, the "clean the filter" timer is broken and needs replacing.