Question about Goodman GMS90703BXA Heater
The condensor will run but the blower will not start. however the blower works fine on heat. Help!
I would also check the "G" wire at the Thermostat and make sure that it has a solid connection. The other end screws on to a terminal in the furnace. Check this connection as well. This green(G) wire is what activates the 120v relay on the circuit board. You can test this by turning the thermostat to the off position and then jumping the 24v R terminal with the 24v G terminal at the furnace. if the fan comes on then the problem is in the thermostat wire or the thermostat itself.
Posted on Jun 15, 2008
Check the wires coming from the blower motor. Find the one going to "Cool" on the circuit board. Make sure it has a good connection. You can also try and removing a wire that is now on "Park" and putting it on "Cool" and see if that helps. If it does, you have a bad motor. If nothing changes, I suspect a bad circuit board or fan relay on the A/C side of the unit. It may take a technician to diagnose, sorry.
Posted on Jun 10, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 31, 2015 | Heating & Cooling
Sep 07, 2014 | Carrier Heating & Cooling
Feb 03, 2013 | LG LS-L1210CL Mini Split Air Conditioner
Nov 08, 2010 | Heating & Cooling
Jun 11, 2010 | Whirlpool Electronic Window Air...
Aug 09, 2009 | Dometic 57915531 Air Conditioner
Jul 26, 2009 | Heating & Cooling
Jul 20, 2009 | Dometic Rooftop RV Air Conditioner
Jun 28, 2009 | Heating & Cooling
Aug 12, 2008 | Carrier Heating & Cooling
272 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: