Question about Ruud Central System Air Conditioner
My air conditioner stopped working yesterday. I went to check the circuit break case and saw that the one for the air conditioner was tripped. I switched it all the way to the off position then back to the on position. I turned on t
If breaker won't hold compressor is not going bad it is. A simple way to chech your breaker: Make sure breaker is off. Turn power off at outside disconnect. Disconnect the high voltage leads from the incoming at the contactor. Wire nut them. Turn the breaker back on. If it stays engaged you know its not the breaker and you confirm it is the compressor....
Posted on Jul 03, 2008
Your compressor could be going bad. You would need to check to amp draw on the the leads coming out of the compressor. There is a maximum rating listed on data plate. Something simple could be that your condenser the out side part of the unit is dirty. All you have to do is turn off the shut off switch out side, get a hose and some dish soap and wash the coils. Be careful with the water presssure not to bend the fins. Or some thing even a lot of techs look over is the breaker is bad.
Posted on Jun 09, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 27, 2015 | Heating & Cooling
Jul 07, 2014 | Panasonic Heating & Cooling
Jul 29, 2011 | Maytag M6P09S2B Portable Air Conditioner
Aug 09, 2009 | Dometic 57915531 Air Conditioner
2,034 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: