Question about Hampton Bay HBLG5004 Air Conditioner
I would deffinatly change the Capacitor. They are normally a dual run type. One terminal runs the fan motor, the other runs HERM or compressor & C terminal is the common for both. Capacitor can be either round or oval if space permits, but make sure the UF numbers & VAC numbers are the same. You can if you must go higher on the VAC number, but not lower. But is best to get exact values. Fan motors with oiled clean moving shaft that hum are either burnt out capacitor or fan motor winding is bad if capacitor change does not work. Avg cap. price is Aprox $16-$20.00.
Posted on Jul 21, 2008
Had this problem....you need new fan motor if capacitor is good...motor is overheating and the safety is kicking it off...replace
Posted on Jun 22, 2008
Might want to check the fan motor start capacitor
Posted on Jun 09, 2008
SOURCE: FAN MOTOR
The run capacitor is probably bad. The run capacitor is usually a two part component. One part serves the fan and one part serves the compressor. Sometimes when they fail the fan will even run backwards instead of just stalling. Replace it.
Posted on Jan 13, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 14, 2010 | Fujitsu Heating & Cooling
Aug 10, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Dec 24, 2009 | Heating & Cooling
Oct 02, 2009 | Dometic Rooftop RV Air Conditioner
Sep 12, 2009 | Windchaser 3-way Oscillating Fan
Aug 18, 2009 | Dryers
Jul 16, 2009 | Heating & Cooling
Jul 01, 2009 | Dryers
Apr 26, 2009 | Heating & Cooling
Nov 18, 2007 | Hampton Bay 36 In. San Marino in Brushed...
561 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: