Question about Amana Air Conditioners
Http://www.amana-hac.com/ This site has a means of contacting them to get information under products, and heating.
Posted on Jun 08, 2008
Tips for a great answer:
Mar 14, 2014 | Goodman Air Conditioners
Jan 01, 2013 | Amana Distinctions 95% Gas Furnace...
Mar 21, 2011 | Air Conditioners
You need to find out if the problem is in the T-stat, T-stat wire or in the furnace you can do this in a few easy steps
Step 1- Unwire the low voltage from the furnace. Then turn the power back on and see if the blower comes on if it does then the problem is in the furnace and you will need to troubleshoot the furnace (see bottom of page for troubleshooting furnace) if it does not then proceed to step 2
Step 2- Wire the low voltage back up to the furnace (follow the wiring diagram below). And unwire the T-stat, make sure that no wires are touching each other, then turn the power back on to the furnace, if the blower starts then you have a short in the T-stat wire and you will need to pull a new wire. If it does not then proceed to step 3
Step 3- Turn the power back off at the furnace and wire the T-stat back up (follow the wiring diagram below). Turn the T-stat to auto heat 90 if the heat does not start but the blower just runs then you need to replace the T-stat.
Nov 24, 2010 | Comfort-Aire Air Conditioners
Mar 06, 2010 | Amana Haier AP125HD Air Conditioner
Sep 21, 2009 | Ruud UBHC Air Conditioner
Nov 15, 2008 | Amana Air Conditioners
Nov 12, 2008 | Amana Air Conditioners
Sep 16, 2008 | Amana Air Conditioners
Oct 10, 2016 | Amana Air Conditioners
501 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: