Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
First check the breaker. If it has been tripped then you will surely need a good contractor.
If it has not tripped then double check the thermostat settings and batteries (if applicable). Make sure the fan is set to auto, The cool function has been selected and the temperature has been set low enough for the unit to come on.
If this still does not work then you will still need a technician. This is because there are many more possible failures all of which are relatively dangerous and technical. Good luck!
Posted on Jun 18, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 13, 2014 | Heating & Cooling
May 12, 2017 | Heating & Cooling
How do you know power is at the outdoor unit? Did you check it with a meter? Check your breaker. If there's power at the outdoor unit, then shut the power and test your contacter. If the contacter has supply power then check the low voltage (24-28 volts) that operates the contacter, and if none check the low pressure cut-out,high pressure cut-out and make sure the thermostat is calling for cool. All ok so far, then test your capacitor. I forgot to mention to check for loose, broken, and disconnected wires.
Aug 24, 2013 | Carrier Heating & Cooling
May 09, 2012 | Heating & Cooling
Mar 22, 2012 | Carrier Heating & Cooling
Sep 07, 2011 | Heating & Cooling
Jun 10, 2010 | Heating & Cooling
Mar 08, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Sep 18, 2008 | Heating & Cooling
117 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: