Question about Heating & Cooling
The unit inside turns on and blows...my unit outside will not turn on i can hear a click but nothing else..it was just put in (the whole unit inside and out..we double checked power and lines..charged it ..but itstill wont run??? Please help
WARNING THIS A DANGEROUS REPAIR DON'T TRY IT UNLESS YOUR QUALIFIED TO WORK ON HIGH VOLTAGE!!
Tip: Never complete a 220v< circuit with your vascular system.
New Unit? wow wheres the installer? kk I'm assuming thats a dead end for some reason. Check for 220v at the compressor relay. I'm gonna go out on a limb and say your not getting the 220v power that you need to operate the unit. Do you have other 220v appliances such as a dryer or stove, if they are working properly that means that both legs of the 220v are making it from the pole to the house. Is the wiring in the breaker panel to the breaker that protects your condenser secure and tight. Are you getting 220v to that breaker? Is the wiring in the disconnect box by the condenser secure and tight? Are you getting 220v there? Is the connections to the compressor relay secure and tight are you getting 220v there. Is the compressor relay closing and are you getting 220v to the compressor? See how this works. Lol, Fun isn't it GL I hope this helped.
Posted on Jun 08, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
Jun 16, 2012 | Carrier Heating & Cooling
Sep 03, 2011 | Ruud Heating & Cooling
May 18, 2011 | Goodman CKL60AR60 Air Conditioner
Jul 09, 2010 | Carrier 38CKC048 Air Conditioner
Apr 27, 2010 | Carrier 38CKC036 Air Conditioner
Apr 02, 2010 | Carrier 38BRC048 Air Conditioner
Jul 02, 2009 | Honeywell Heating & Cooling
Aug 25, 2008 | Carrier 38CKC042 Air Conditioner
May 12, 2008 | Heating & Cooling
447 people viewed this question
Usually answered in minutes!