Question about Ruud UBHC Air Conditioner
MY outside unit wont come on it just gives a buzzing noise what could be the problem
It sounds like you may have lost line voltage to the unit. What you hear is most likely the buzzing of the compressor relay which is energized by 24v from the indoor unit. Look at your condenser coil, are the aluminum fins clogged with debris? If so this is likely the cause of the tripped breaker and will need to be cleaned. Before you go to the trouble have someone go to your breaker panel and flip all the 220v DPST breakers off and back on while you watch and listen to the condenser to insure that the fan and compressor will come on line as soon as this is confirmed turn the breaker off and clean you condenser coil, the correct way to clean the condenser coil is to remove the disconnect plug at the unit or turn of the line voltage at the breaker, remove the top panel that supports the fan , flip it over being carefull that it's weight is supported in a way that wont stress the wireing harness to the fan motor. Spray the inside surface of the condenser coil with a heavy foaming cleaning solvent and let it have time to saturate the grime compacted between the fins then spray from the inside out and from the top down until the water runs free and clean from the inside thru the coil. Replace the top panel and allow time to insure that any water that might have gotten into the fan motor housing has evaporated, Then start it up if that was the original cause of the thrown breaker (very often is) then your in good shape and just saved a service call, Gratz!
Posted on Jun 08, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 22, 2013 | Ruud Central System Air Conditioner
Aug 06, 2012 | Ruud UBHC Air Conditioner
Jun 16, 2011 | Ruud Matching Split Air Conditioner
Jul 09, 2010 | Ruud UBHC Air Conditioner
Oct 19, 2009 | Ruud UBHC Air Conditioner
Aug 10, 2009 | Ruud UAKA037 Air Conditioner
Jun 19, 2009 | Ruud UAKA037 Air Conditioner
May 28, 2008 | Ruud Matching Split Air Conditioner
May 16, 2008 | Ruud UAKA030 Air Conditioner
147 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: