Question about Honeywell Power Humidifier: Furnace Humidifier/ Humidifier
Trane literature says when the thermostat is set to 'on', the furnace fan will operate for the cost of a 60 watt bulb. I know four Trane owners (units less than 2 years old) and only one of the four operates at that level....the rest are operating at approximately 350 watts and it is cost prohibitave to run. I want to get full benefit of my electronic filter. Local service techs say they don't have a solution...Trane headquarter techs say it is in the IFC. They did not say if it can be tweaked.
If the furnace is a vairable speed furnace you have to make sure that all you dip switches are in the correct position on the lower furnace door there will be a label that gives you info on how to boost cfm and other info if you look at this label you will find a comfort R setting this is what you want to set to get the lowest fan setting but it does have to be a vairable moter
Posted on Feb 23, 2009
If the manufacture says it is the IFC then you should have the IFC checked by the company who installed it if it is under warranty still
Posted on Feb 16, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The filter should be located below the tank. the tank should lift off of the unit and there should be a rectangular cavity where the filter fits. You will most likely find the old filter dried up and filled with a white crust. That is salt and other minerals in the tap water that the filter catches.
Posted on Feb 11, 2008
SOURCE: Furnace blower blows cold air
It is possible that you did not set the new blower on the proper speed. Black wire is high. Blue is medium. Red is low. If the fan is operating to slow it can run to hot and trip the high limit control. Make sure the filters are clean. When the old motor went bad, the problem might not have been discovered rite away your high limit control might need to be changed.
Also anytime you work on a furnace you can kick up some dust. Always clean the flame sensor.
Posted on Mar 08, 2009
Tips for a great answer:
Oct 28, 2016 | Humidifiers
Dec 13, 2009 | Aprilaire 700 Humidifier
Oct 08, 2009 | Honeywell Power Humidifier: Furnace...
Mar 08, 2009 | Honeywell Power Humidifier: Furnace...
Feb 07, 2009 | Aprilaire 550 Humidifier
Jan 03, 2009 | Aprilaire 550 Humidifier
Nov 23, 2008 | Aprilaire 600 Humidifier
Nov 10, 2008 | Aprilaire 600 Humidifier
Nov 29, 2007 | Honeywell Power Humidifier: Furnace...
Dec 15, 2014 | Honeywell Power Humidifier: Furnace...
1,320 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: