Question about Ruud UBHC Air Conditioner
Does the fan on the outdoor condensing unit come on when the compressor does? If so, Is the condenser coil clean so that the airflow from the fan can remove heat from the condenser coil so the compressor won't overheat and trip the internal overload compressor protection circuit? If yes then is the indoor evaporator fan working properly? If yes are your filters clear and evaporator coil clear so that adequate air is flowing over the coil to prevent the compressor low pressure protection circuit from tripping? If so is the refrigerant charge on the system correct- either overcharged or undercharged can trip the compressor protection circuit. By now you should have come across an explanation for your compressor short cycling. If I had to guess I would bet on inadequate airflow over the condenser coil do to a faulty condenser fan motor either not turning at all or turning for a few minutes and then stopping when it overheats. This is likely caused by an unsealed replacment motor being used outdoors and water/rust has accumulated over the winter season and/or the capacitor is bad (in this case the motor may be turning slowly backwards) or just plain old worn out. I hope this helps get you to cold air sometime soon GL!
Posted on Jun 10, 2008
Tips for a great answer:
Jun 20, 2014 | Ruud Air Conditioners
Mar 20, 2011 | Air Conditioners
Jul 25, 2010 | Ruud UBHC Air Conditioner
Mar 28, 2010 | Ruud Handler Air Conditioner
Sep 13, 2009 | Ruud UBHC Air Conditioner
May 31, 2009 | Ruud UBHC Air Conditioner
Jul 05, 2008 | Ruud UBHC Air Conditioner
321 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: