Question about Heating & Cooling
Ive lost pressure so have no hot water or anything how do i get the pressure back?
On the pipework near the boiler there should be a silver flexi hose connecting the two copper pipes ...this is called a filling loop there sould be taps on the filling loop turn on by moving the black plastic taps do this slow ..at the same time look at the pressure gauge on a baxi do not go over 1 bar...............
warning ..if the boiler has lost pressure where has it gone..is there any leaks anywhere..if it persist contact a engineer
Posted on Jul 07, 2008
Heating Is a closed system, so if its loosing water that fast , must be a leak somewhere, look for green scale on pipework joints, or rusty spots around radiator, espescialy around the bleed valves and plugs at the top, also check the red pressure relief is not stuck open, turn it untill it 'clicks' shut to be sure. When filling fill up to about 1.5 bar then run system warm and go round bleed each radiator, highest first, then top up to about 1.5 warm.
Posted on Jan 01, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 02, 2012 | Heating & Cooling
Nov 04, 2010 | Heating & Cooling
Aug 16, 2010 | Heating & Cooling
Aug 07, 2010 | Heating & Cooling
Mar 31, 2010 | Heating & Cooling
Mar 03, 2010 | Heating & Cooling
Feb 01, 2010 | Heating & Cooling
Jan 24, 2010 | Desa International CBN30T Central Heating...
654 people viewed this question
Usually answered in minutes!