Question about York Furnace Draft Inducer Blower Fasco # A224
Make sure there is water in the drain trap. If the drain is "WIDE OPEN" the fan can draw air from the trap and not from outside, and the pressure differential will not be enough. This happens as the trap dries out over the summer, then when you start the furnace, the condensate drain from the fan is dry.On some furnaces this trap is a square box,anyway fill that tubing till you see water running to drain.If you read your manual it should tell you to prime the trap. Position of the switch, shouldn't matter, as it is s diaphragm that the vacuum pulls on to engage the switch. You're probably close to the setting, and by just moving the switch, made it operate.
Posted on Oct 17, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 20, 2015 | 2007 GMC Envoy Denali
on Dec 20, 2016 | Cars & Trucks
Apr 18, 2013 | Heating & Cooling
Jan 03, 2011 | Heating & Cooling
Oct 08, 2010 | York Furnace Draft Inducer Blower Fasco #...
Dec 12, 2009 | Coleman Heating & Cooling
Nov 28, 2009 | York Furnace Draft Inducer Blower Fasco #...
Oct 16, 2009 | York Furnace Draft Inducer Blower Fasco #...
Nov 19, 2008 | Heating & Cooling
Nov 18, 2013 | York Furnace Draft Inducer Blower Fasco #...
316 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: