Question about Goodman GMS90703BXA Heater
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Goodman Furnace GMP 050-03
You need to check for 24 volts across the gas valve as the ignitor glows. If you get it, it is a bad gas valve. If there is no voltage or strange voltage, replace the control board.
Posted on Dec 10, 2008
Call AAA back it should be warrented if they worked on it frst don't touch it or you lose your warrent, it does sound like the thermal bulb is not in the flame so call them back fist then let me know post here and I will try to help you if they do not sove the problem, you should have a work order they gave you when they did the repair. Hold on to it.
Posted on Oct 09, 2009
Testimonial: "The thermal bulb would cause the twinning light to come on."
sounds like the primary limit typically behind the gas valve its larger then the others, rectangle in shape with 2 wires going to it. be careful if your bypassing limit this can create a very hazardous condition
Posted on Nov 06, 2009
Usually you can find the control board on the lower part of the furnace. Turn the power off and remove the
doors. This board is usually located directly in front of the blower motor.
On the control board locate the terminals marked heat/cool/park and Park Lets say the Heat Terminal
has a red wire attached to it and you want a higher
Red is uasually low speed, remover the red wire from
heat terminal and exchange it with a wire attached to
a terminal lab eled park. Black is usually high spped
Posted on Jan 02, 2010
Tips for a great answer:
Oct 12, 2014 | Heating & Cooling
Jun 12, 2012 | Goodman Heating & Cooling
Sep 08, 2011 | Heating & Cooling
Apr 02, 2011 | Goodman Heating & Cooling
Feb 09, 2011 | Goodman Heating & Cooling
Jan 26, 2011 | Goodman CACF048B2A Air Conditioner
Nov 08, 2010 | Goodman GMS90703BXA Heater
Feb 15, 2010 | Heating & Cooling
Nov 06, 2009 | Goodman GDS80904BNA Open Flame Heater
Nov 04, 2009 | Goodman GDS80904BNA Open Flame Heater
105 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: