Question about Soleus Heating & Cooling
First off you need to check the filters inside of the home, if they are dirty replace them. I would also check the condenser outside and see if it has a high pressure reset, this is usually on the smaller of the two copper lines coming from the compressor. It will look like a small valve with a button on the top or it will be in a gray case with a small metal stem that may be pushed in to reset. If the high pressure switch has been tripped most likley the condenser is dirty and it will need cleaned. To do this turn off the disconnect to the condenser, take the case apart to gain access using a garden hose rinse from the inside out thourghly.
Posted on Jun 10, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 15, 2014 | Dometic DM2652 Americana Fridge...
Mar 02, 2014 | Dometic Refrigerators
Sep 29, 2011 | Dometic RM2652 Refrigerator
Jul 12, 2010 | Summit Commercial Refrigerators
Jun 30, 2010 | Vinotheque Whisperkool 4200 Wine Cooling...
May 24, 2010 | Dometic RM2852 Refrigerator
Mar 28, 2010 | Thetford RV Refrigerator - N300 Model -...
Sep 18, 2009 | Refrigerators
Dec 28, 2007 | Thetford Norcold DE0051 Refrigerator
364 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: