Question about Air Conditioners
Hello from KOOLBREEZES, this is a simle problem and easy to fix. You have 2-lines going to / from your outside unit. a SMALL COPPER -line and a LARGE COPPER line with insulations. The fat line is suppose to have moisture on it wheres it,s not insulated which tells you you have enough refrigerant gas comming back to he compressor but if its dry you,re low on freon and need a charge or the outside condenser is dirty and not getting rid of enough heat!
Posted on Jun 02, 2008
Tips for a great answer:
Aug 12, 2014 | Air Conditioners
Jul 06, 2012 | Carrier 38CKC036 Air Conditioner
Jun 28, 2011 | Goodman CLQ30AR32 Air Conditioner
Sep 07, 2010 | Goodman CLJ30AR32 Air Conditioner
Aug 05, 2010 | Air Conditioners
Jul 18, 2010 | Goodman CLQ36AR49 Air Conditioner
Jul 07, 2010 | Kenmore 75085 Air Conditioner
Aug 19, 2009 | Goodman Air Conditioners
Mar 25, 2009 | Air Conditioners
244 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: