Question about Heating & Cooling
Hello from KOOLBREEZES, this is a simle problem and easy to fix. You have 2-lines going to / from your outside unit. a SMALL COPPER -line and a LARGE COPPER line with insulations. The fat line is suppose to have moisture on it wheres it,s not insulated which tells you you have enough refrigerant gas comming back to he compressor but if its dry you,re low on freon and need a charge or the outside condenser is dirty and not getting rid of enough heat!
Posted on Jun 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 19, 2014 | Honeywell CT500 Digital Heat / Cool Manual...
Aug 12, 2014 | Heating & Cooling
Jul 06, 2012 | Carrier 38CKC036 Air Conditioner
Jun 28, 2011 | Goodman CLQ30AR32 Air Conditioner
Jan 03, 2011 | Goodman Heating & Cooling
Sep 07, 2010 | Goodman CLJ30AR32 Air Conditioner
Aug 05, 2010 | Heating & Cooling
Jul 07, 2010 | Kenmore 75085 Air Conditioner
Mar 25, 2009 | Heating & Cooling
244 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: