Question about Heating & Cooling
The Condensor unit won't come on except if you push down the contactor manually. Over the winter the inside heater and air handling part of the split system was replaced with a Goodman unit. The outside part of the split system was not touched. It worked well last year. Any ideas?
It sounds to me that the wire going to y2 on the furnance coming from the thermostat was not wired back up this is the wire that supplies control voltage to the contactor on the condensing unit. I would call the installer who changed the furnace out back to remedy this problem.
Posted on Jun 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 03, 2011 | Ruud Heating & Cooling
Jun 23, 2010 | Ruud UAKA030 Air Conditioner
Apr 03, 2010 | Ruud Central System Air Conditioner
Oct 10, 2009 | Ruud Central System Air Conditioner
Sep 04, 2009 | Ruud UBHC Air Conditioner
Jul 24, 2009 | Mitsubishi MXZ30TN Air Conditioner
Jun 13, 2009 | Weather King 10AJA3601AH Air Conditioner
Mar 23, 2009 | Ruud Central System Air Conditioner
136 people viewed this question
Usually answered in minutes!