Question about APC - UPS - Matix/Symmetra Enterprise UPS Symmetra 12KVA Expandable to 16kVA N+1 Master Frame (SY12KEX) UPS System
Without knowing the full model number of your UPS I cannot go into specific details fully for you.. but a good test with any 'intelligence module fault' is to re-seat the module and run a self test. If the fault remains then your intelligence module is bad and you will need to acquire a new one to replace the faulty one. This can all be done 'on-line' and you should not have any downtime... assuming there is a redundant intelligence module in the unit which is normally the case. This will clear the fault.
If you would like more information give me a call: 407.380.9200.
Posted on Nov 01, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a symmetra RM
The first thing is to make sure the interconnection between the main module and the extended run is properly making contact
Next is to verify the XR battery cabinet voltage is according the battery charging voltage (normally 137 Vdc). Power View will confirm this voltage.
My favorite is to load test the batteries module individually and make sure the batteries are good.
If there is a +/- 3 volts difference between the UPS and the extended run module E0 alarm would be indcated.
Posted on Apr 02, 2011
Tips for a great answer:
Jan 17, 2014 | APC Symmetra PX SY64K160H UPS System
Aug 31, 2012 | APC Symmetra Tune-UPS technical support -...
Nov 03, 2010 | APC Symmetra Tune-UPS technical support -...
Nov 13, 2009 | APC - UPS - Matix/Symmetra Enterprise UPS...
1,423 people viewed this question
Usually answered in minutes!