Question about Rheem 266K to 399K BTU Swimming Pool Natural Gas Heater ()
"CFH" is Call for heat. That means your heater is trying to fire (not an error code). "HL2" is an error code which stands for "High limit #2". This error means the water in the heat exchanger is too hot,and the heater shuts itself down to prevent damage. Most common causes are poor water flow .Make sure the correct pump is running,and you have at least 10psi on the filter gauge. also be sure that the bypass valve is at least 1/2 way closed.The Bypass valve is located on the return line after the filter just passed the first tee.
Posted on Oct 13, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 21, 2015 | Raypak RP2100 DIGITAL POOL HEATER R265
May 25, 2014 | Rheem 266K to 399K BTU Swimming Pool...
Aug 18, 2013 | Rheem 266K to 399K BTU Swimming Pool...
Dec 16, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Aug 03, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Mar 16, 2009 | Bosch 1600H-LP Liquid Propane AquaStar...
Mar 16, 2009 | Ruud Central System Air Conditioner
543 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: