Question about Goodman GMS90703BXA Heater
Just put in a new 3 ton system, compressor and outside fan won't start contacts are engaged. and it has power 120 both sides.
The unit is a GSH 130361a
YOU CAN HAVE 120 ON EACH LEG WITHOUT HAVING 240 ACROSS CHECK ACROSS BOLTH LEGS.IF YOU HAVE 240 YOU PROBABLY HAVE A SAFETY HOLDING IT OUT.TRACE THE POWER FROM THE CONTACTOR THREW THE BOARD BY HOLDING ONE METER LEG ON COMMON AND WALKING THREW THE CIRCUIT WITH THE OTHER LEG.
Posted on Jun 06, 2008
Safety switch or circuit board.
Posted on Jun 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 17, 2011 | Heating & Cooling
Aug 11, 2010 | Goodman CLQ36AR49 Air Conditioner
Jul 09, 2010 | Carrier 38CKC048 Air Conditioner
Jun 15, 2010 | Sanyo CMH2472 Air Conditioner
Apr 02, 2010 | Heating & Cooling
Oct 08, 2009 | Ruud Central System Air Conditioner
Jun 25, 2009 | Ruud UAMB Air Conditioner
Jun 11, 2009 | Goodman CKL60AR60 Air Conditioner
Nov 29, 2008 | Panasonic Heating & Cooling
May 28, 2008 | Ruud Matching Split Air Conditioner
59 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: