Question about LG Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
1. Do not set the aircon too low temperature in overcast weather, this will cause ice ups and water dripping. Optimal comfort zone temperature is 24c.
2. You need to open the grill cover on the front of the aircon which unclips either end left and right with a finger pressure. You will find two filters which can slide out and should be cleaned. First tap them together to remove dust, then you can wash them with mild soap and cold water.
3. There is the third possibility that an insect has made a nest in the drainpipe. You should look on the outside of the building and locate a plastic drainpipe. You can either blow into this pipe with your mouth or get a blower. This will unblock any restriction in the drainpipe.
Goodluck and ratemeplease.
Posted on Mar 19, 2009
E-5 -Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 03, 2011
Tips for a great answer:
Jan 02, 2014 | LG LS-K2430HL Heat Cool Mini Split Air...
Jan 18, 2013 | LG LSC121PMA Split System Air Conditioner
Feb 15, 2011 | LG LS-J0910HL Heat & Cool Mini Split Air...
Dec 31, 2010 | LG LSC121PMA Split System Air Conditioner
Aug 10, 2010 | Hitachi RAS-09UH Air Conditioner
Apr 17, 2010 | LG LS-L1210CL Mini Split Air Conditioner
May 23, 2009 | LG Heating & Cooling
Mar 19, 2009 | LG LSC121PMA Split System Air Conditioner
Feb 01, 2009 | LG LS-K1830CL Cool Mini Split Air...
414 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: