Question about Computers & Internet
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: APC Smart-UPS 1500VA
yeppers...those APC units sometimes kick the monitoring software. sometimes you need to unhook the connection cables(like a reset) so that the firmware can 'unlock' which can cause that christmas tree effect on the panel lights.
Posted on Feb 06, 2008
i think by replacing the battery has not been the solution to the problem
u need to check the battery charging voltage when turned ON with main electricity, if no voltage present from charger, there is no question of battery getting charged and also once the battery is down with charge it may not re charge hence the indicator and alarm.
recomended to nearest service centre
Posted on Sep 13, 2008
SOURCE: APC Smart UPS 3000VA - Dead UPS
ok how long you brought the ups and how long you had not start the the ups usaully ups is power dead change the battery and try to power up it should work be sure that all connection is connect properly before power up the ups.. if the ups doest work that will be the mainboard problem you hav to call for vedor to repair the unit.. yes these fuse for the ups but it unlikely to be blown so should worry of the fuse it self.. change of battery come with different spefc for the ups.. eg su3000rmi3u, sua3000rmi3u, su3000rmxl3u --- battery replacement is 8 pcs of 12v 7ah. sua3000rmi2u-- 6 pcs of 12v 7ah or 8 pcs 12v 5ah. su3000rminet-- 4 pcs 12v 17ah,
Posted on Mar 28, 2009
It could be that the cable to the front-panel got damaged during the battery replacement. After all these years you would think APC would improve that aspect of their design. All I can suggest is inspecting the cable and where it connects to the front panel.
Posted on Apr 26, 2009
Tips for a great answer:
Jun 23, 2014 | APC Smart-UPS RT 5000VA (SURTD5000XLI) UPS...
Mar 31, 2014 | APC Back-UPS XS900 (BX900) UPS System
Aug 15, 2011 | APC Smart-UPS 1000VA UPS System
Aug 14, 2011 | APC Smart-UPS RT 10000VA - UPS ( external...
May 21, 2010 | APC Smart-UPS 1000VA UPS System
May 06, 2010 | APC Smart-UPS 1500VA Shipboard...
Apr 18, 2009 | APC Smart-UPS 1000VA UPS System
Apr 01, 2009 | APC Smart-UPS 1000VA UPS System
999 people viewed this question
Usually answered in minutes!