Question about All-Pro SPC-85 Utility Heater
Yes this is probably the thermocouple connection.
Just remove the end of the thermocouple from where is goes into the gas valve and leave the end that goes into the flame in place.
Clean the end of the thermocouple connect by scraping off just a little metal from the end just about there the nut tightens the thermocouple into the gas valve. After you have exposed some new metal do the same inside the valve where the thermocouple seats into the gas valve.
Use a small pic or similar item to scrape inside the gas valve to expose some new metal there also.
Now reassemble the thermocouple into the gas valve and see if the heater works.
Here is a link with some more instructions.
Posted on Oct 10, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 13, 2016 | Heating & Cooling
May 29, 2016 | Heating & Cooling
Feb 08, 2015 | Heating & Cooling
Nov 18, 2014 | All-Pro Heating & Cooling
Jan 06, 2011 | All-Pro Propane Garage Shop Heaters - All...
Jan 04, 2011 | All-Pro Propane Garage Shop Heaters - All...
Nov 11, 2010 | All-Pro Propane Garage Shop Heaters - All...
Jul 28, 2010 | Reddy HEATER RLP30 30,000-BTU PORTABLE LP...
Jan 22, 2010 | Reddy HEATER RLP30 30,000-BTU PORTABLE LP...
Nov 21, 2009 | All-Pro Propane Garage Shop Heaters - All...
1,653 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: